Payment & Shipping Terms:
|Event Recording:||Providing The Rich Data Support For System Fault Analysis||Work Time In Rainy Weather:||≥10 Days|
|Function:||Solar Power Supply|
short circuit indicator,
phase loss indicator
communication short-circuit and earth fault indicator with GSM (short messages) and GPRS (data)
Remote terminal uint is the data acquisition and communications forwarding device for power distribution network load monitoring, fault detection and positioning system, which can be set as the practical distribution terminal device of two remote (remote signaling, telemetry) functions in the distribution automation system via terminal parameter configuration, which can also be set as the traditional distribution terminal device of remote fault positioning system.
Remote terminal uint is to process and analyze the information from overhead indicator sent via wireless and then send the circuit load current and fault information to the main distribution network station via GSM short messages or GPRS communication.
|Dimension of repeater station||H×W×T=388mm×366mm×368mm|
|Weight of repeater station||6.75kg|
|Applied voltage grade||7~69kV overhead line|
|Circuit load current||0~630A|
|Rated working voltage||5.5V-7.5V|
|Overall power consumption||＜0.4W|
|Work time in rainy weather||≥10 days|
|Solar panel||Organic glass protection, amorphous silicon, and 30 years of service life|
|Power of solar panel||12W/10V|
|Quantity of cooperation indicators||12|
|GPRS module||E-GSM/GPRS 900/1800 dual band|
|Working temperature range (lead-acid battery)||-35℃～75℃|
|Working temperature range (lithium iron phosphate)||-20℃～75℃|
Introduction of device components:
1. J1 expansion port 1, used to monitor the wireless information received by repeater station.
2. J2 maintenance port, used to set the parameters of repeater station via RS232 connecting line.
3. J4 expansion port 2, used to set the IP address of GPRS module and other relevant parameters.
4. Battery, connecting the battery terminal externally.
5. Mobile phone card slot, embedded GPRS module, used to install the SIM card for wireless communication.
6. Solar power, connecting the power supply terminal of solar panel externally.
Remote terminal uint is to receive the circuit fault information and circuit load operation information from overhead indicator installed in the circuit via wireless for analysis and compiling and then sends the information to main distribution network station via GPRS/GSM communications, to realize the online monitoring, fault detection and positioning functions of distribution network.
There is type test report for it, test items as following:
Type Test Items
|1. appearance and structure 2.function 3. electrical device performance 4.low temperature performance 5.high temperature performance 6.alternating temperature humidity7.vibrationendurance 8.incline drop test 9. electrical device life 10. static electricity and elecro-discharge immunity test 11.radio frequency electromagnetic field radiated immunity test 12.surge impact immunity test 13. power frequency magnetic field immunity test. 14. Adjacent interference test 15.short-circuit withstand impact test 16. fire hazard test 17. power consumption test 18. protection grade test 19. gripping strength test of grip structure.|
Contact Person: Kitty