Payment & Shipping Terms:
|Operating Environment::||no Explosive And Flammable Materials, No Air Or Conductive Dust Which Will Damage The Insulation And Cause Metal Corrosion, No Serious Mold And No Severe Vibration Sources, With Measures To Defend Against Rain, Snow, Wind, Sand, Dust And Static Electricit||Atmospheric Pressure:||66kPa～108kPa.|
|Insulation Impedance:||＞100MΩ/ DC500V;3.On-off Input Circuit To Ground||Power Frequency Withstand Voltage:||1500;Between On-off Input Circuit And Output Circuit|
|Impulse Withstand Voltage:||5k;AC Circuit To Ground||Other Name:||Feeder Remote Terminal Unit|
feeder remote terminal unit,
dsp digital signal processor
remote controlling power distribution feeder terminal unit detecting fault and transmitting switch status data by gprs/3
This is a new HV switch control device equipped with both the imported DSP high-speed sampling chips and the high-performance ARM chips, and can fast and stably finish the monitoring on the switch. It boasts of such functions as the protection, measuring, controlling, monitoring, communication, remote control and so on and features high integration level, flexible configuration and user-friendly interface, widely applied to the radiant and ring network power supply systems to help the systems identify transient and permanent line faults, eliminate the impact of transient line faults automatically, isolate the permanent fault segments to avoid prolonged power failure in large area, and automatically recover the power supply in fault-free areas, so as to realize the automation of power distribution network in a economical and practical way.
CLOSE: Closing button. Press this button, and the device will carry out closing operation.
OPEN: Opening button. Press this button, and the device will carry out opening operation.
START: Start (activate the battery). When PT has no power and the battery switch is "On", press and hold this button for more than 2 seconds to start the battery as the power supply, and then the device can be operated. Note: This button is invalid when there is no battery.
RESET: Reset button. Undefined.
VIEW: Viewing button. Press this button, and enter the relevant operating interface of LCD.
SET: Setting button. While setting the parameters, press this button to save the set parameters.
ENT: Enter button. Selection and enter button. Select and confirm corresponding functions or operations.
ESC: Exit button. It is used for canceling the current operation, exiting the current interface.
: Direction button. It is used for selecting the next one.
: Direction button. It is used for selecting the former one.
Other buttons: the other buttons are all number buttons. While pressing the number button, the lattice LCD will show the corresponding number.
The switch and the device must be loaded and fastened in a closed packing case to prevent overturn or tilt during the transportation
The device shall be stored at a dry, ventilated, moistureproof, shockproof and noxious-gas-proof indoor place. Check if the environment meets the requirement if the device will be stored for a long time. Packing, unpacking and storage shall all be carried out in a dry indoor environment. Please check if the product and its parts are complete and accordant. The product shall not be overlapped over three layers.
Check if the package of the device is damaged.
Check if there is obvious fracture or damage on the surface of the equipment.
Check if the name of the product conforms to the order.
Check if the files, fittings and spare parts are complete according to the packing list of the product.
Check if the technical parameters on the nameplate conform to the order.
Table for Statuses of Indicators on the Pane
|Opened||The switch is in opening status||None||The switch is not in opening status|
|Closed||The switch is in closing status||None||The switch is not in closing status|
|Reclose||The switch is in reclosing reclaim timing status||None||The switch is not in reclosing reclaim timing status|
|Y-Delay||Y during the delay time||None||No timing|
|X-Delay||X during the delay time||None||No timing|
|Circuit||Green: normal circuit/ Red: abnormal circuit||None||None|
|Operation||Abnormal device system||Normal device system||Abnormal device system|
|Power||Power supply is normal||None||The device is out of power or has fault|
|Earthing Fault||Earthing fault||None||Normal earthing|
|Phase fault||Phase-to-phase fault||None||Normal phase-to-phase condition|
|Lockout||The device is locked out||None||The device is not locked out|
|Transient Fault||The device had a fault (The indicator will be off by pressing ESC)||None||The device does not have a fault or the fault has been eliminated|
Contact Person: angel