Sales & Support
Request A Quote -
Payment & Shipping Terms:
|Function:||Detect Earthed Fault||Transmitalarm Signal:||To Panel Indicator|
|Optical Fiber Data Rate:||9600bps||Characteristics:||Automatically Distinguish Fault Current|
underground power cable locator,
cable fault distance locator
TYHD-1 cable earthed fault indicator is applied to cable system below 35KV, with function of zero-sequence current measurement and data transmit function, it indicates fault when earth fault happened in cable, It can help line finder find the fault quickly .shorten power-off time,improve the reliability of power supply,be convenient for users to monitor the zero-sequence load current of line on real time.The picture of product is below:
Using specially designed open zero-sequence CT as sensor of measuring zero-sequence current, micro-power consumption intelligent controlling chip is as core to real-time measure zero-sequence current online and timely transmit current data measured through optical data interface. When earth fault happen, indicator will automatically distinguish fault current characteristics to judge earth fault intelligently, then transmit the data through “data remote transmit interface” and “panel indicator interface”connecting to DTU and panel indicator through the plastics optical fiber to realize remote transmitting for fault signal and measured data.
Install and operation instruction:
install method as following diagram
Loosen the indicator hoop screw and the end connecting line, cover the indicator iron core on cable as diagram, screw indicator hoop again and connecting line.
After indicator fixed, connect indicator’s data remote transmission interface to cable DTU through short-distance fiber optical fiber; connect indicator’s “pulse port”to panel indicator through short-distance plastic optical fiber(notice: if without panel indicator,this interface will not be connected); make sure plastic optical fiber completely connected to the end and screw tightly and well. Optical fiber length is below 15m generally, optical fiber section is cut flat with a cutting knife, is good use for optical signal transmission.
1,Install and uninstall simply.adaptable to detect zero-sequence current in three-phase cable with outer diameter below 110mm.
2,Epoxy resin casting,adaptable to run outside in a long term.
3,Real-time detect zero-sequence current.
4,detect earthed fault
There is type test report for it, test items as following:
Type Test Items
|1. appearance and structure 2.function 3. electrical device performance 4.low temperature performance 5.high temperature performance 6.alternating temperature humidity7.vibrationendurance 8.incline drop test 9. electrical device life 10. static electricity and elecro-discharge immunity test 11.radio frequency electromagnetic field radiated immunity test 12.surge impact immunity test 13. power frequency magnetic field immunity test. 14. Adjacent interference test 15.short-circuit withstand impact test 16. fire hazard test 17. power consumption test 18. protection grade test 19. gripping strength test of grip structure.|